Ban the Can
Why you should avoid recessed lights
One hates to overstate how problematic recessed lights can be, but… they sure are a pain in the energy-auditor butt. There are worse problems (wet basements), more expensive ones (insulating a complicated roof line), and more frustrating ones (the cross-purposes of energy evaluations and homeowner desires). But few elements of the house combine all three in as tidy a package as recessed light cans.
Recessed lights can be an problem. A large, incredibly leaky problem. Of the 10 worst blower-door numbers I’ve seen in newer houses, all 10 involved recessed light installations. A lousy blower-door testTest used to determine a home’s airtightness: a powerful fan is mounted in an exterior door opening and used to pressurize or depressurize the house. By measuring the force needed to maintain a certain pressure difference, a measure of the home’s airtightness can be determined. Operating the blower door also exaggerates air leakage and permits a weatherization contractor to find and seal those leakage areas. means loads of conditioned air escaping the house and uncomfortable homeowners.
Fixing recessed can air leaks can either be an enormous project or an actually impossible project. You would either replace all the cans with airtight ones or build drywall boxes from overhead. Oh, wait? You don’t have access to the recessed cans?
And good luck if they’ve been installed in a cathedral ceiling.
The final hurdle is that there’s a good chance that your customer likes them. You’ve tromped around for three hours, waved your thermal camera about and calmly declared that the homeowner’s sleek modern recessed lights are a big problem. It will always be a difficult conversation.
BLOGS BY ERIC NORTH
Recessed lights: the problems
Why all the venom? The building enclosure is a continuous layer separating the interior from the exterior. The closer the building enclosure is to a uninterrupted whole, the more efficient and comfortable the space will be.
Recessed lights replace ugly ceiling mounts – with the trade-off being that you’ve punched a hole through the building enclosure. Sure, you’ve got a neat, uncluttered interior look. However, you’ve traded a substantial amount of conditioned air leakage for that appearance. The heat is escaping like crazy.
Where a homeowner sees neatness and order, I see a building science atrocity. The fixtures penetrate the air barrierBuilding assembly components that work as a system to restrict air flow through the building envelope. Air barriers may or may not act as a vapor barrier. The air barrier can be on the exterior, the interior of the assembly, or both. and almost always make the house less efficient.
What to do?
You can check out this article for more details on how to air seal existing recessed light cans. But here are a few thoughts:
First, exorcise recessed light cans from your mental vocabulary. There are loads of ways to light your house other than gouging a hole through the air barrier. Once you move away from the recessed cans, you may improve problems associated with the use of recessed cans (like that they are fixed in one spot and pointing straight down).
If you do plan on using recessed lights, consider building a soffit box. This will keep the lighting out of sight without punching holes into your attic. And if you insist on punching a hole into your attic, make sure the recessed can is a non-perforated “sealed” can.
A brief aside on technical building issues
[Warning: Tech talk ahead!]
I like to say materials are tested by very smart guys in lab coats. So-called “airtight” recessed light cans are tested by the ASTMAmerican Society for Testing and Materials. Not-for-profit international standards organization that provides a forum for the development and publication of voluntary technical standards for materials, products, systems, and services. Originally the American Society for Testing and Materials. (American Society for Testing and Materials) using the ASTM E283 test procedure for air leakage. Super sexy.
Non-perforated recessed lights limit air leakage to 2.0 cfm (cubic feet per minute) at 75 pascals of pressure difference. That’s pretty tight; not airtight, but better than older recessed cans. And this type of recessed can fixture is always rated for insulation contact.
[End of warning about tech talk.]
Recessed lights don’t need to be the enemy. But too often they are installed with little care toward their impact on the building enclosure. Look at other options – and if you still go with recessed cans, make sure they’re not trashing the home’s air barrier.
- Erik North
Mon, 02/03/2014 - 13:48
Mon, 02/03/2014 - 16:35
Mon, 02/03/2014 - 20:17
Tue, 02/04/2014 - 11:52
Tue, 02/04/2014 - 12:17
Tue, 02/04/2014 - 18:22
Wed, 02/05/2014 - 18:24
Wed, 02/05/2014 - 18:36
Wed, 02/05/2014 - 19:29
Wed, 02/05/2014 - 20:59
Wed, 02/05/2014 - 21:01
Wed, 02/05/2014 - 22:10
Thu, 02/06/2014 - 09:22
Mon, 02/10/2014 - 08:48
Mon, 02/10/2014 - 13:38
Mon, 06/09/2014 - 10:50
Mon, 06/09/2014 - 11:35