Phantom Electrical Loads With Mitsubishi Minisplit
I recently finished building a pretty good house using a few single zone mitsubishi hyper heat minisplits. The 18K unit I mostly use will draw around 200 watts of electricity even when it is turned off. I don’t like paying for phantom electrical loads. I just noticed this this morning, and will start investigating why this is happening.
Could it be the hyperheat pan? I will see if I can disconnect that .
I also have 2 smaller 9K units that draw about 20-25 watts each when completely off.
Any tips or ideas would be appreciated!
Moses Lake, WA
I have been a dedicated fan/follower of this site for 4-5 years and built my house using much of the advice here.
GBA Detail Library
A collection of one thousand construction details organized by climate and house part