Stay Away from Foil-Faced Bubble Wrap
This R-1 product can be used to make Halloween costumes, but should never be used as insulation
Most brands of foil-faced bubble wrap are only 3/8 inch thick or less, and have an R-valueMeasure of resistance to heat flow; the higher the R-value, the lower the heat loss. The inverse of U-factor. of only 1.0 or 1.1. Since the product often costs more per square foot than 1-inch thick rigid foam rated at R-5, why would anyone use bubble wrap as insulation?
The R-value of foil-faced bubble wrap is so low that it has few, if any, advantages over rigid foam. Of course, the product’s foil facing can be used as a radiant barrier — but if you want a radiant barrier, cheaper products are available. (The bubble wrap layer is unnecessary, since it adds cost to the material without adding any useful thermal performance.)
Exaggerated R-value claims
Since the main benefit from foil-faced bubble wrap is due to its radiant-barrier facing, the product is basically worthless unless it faces an air space. A decade ago, when I was the editor of Energy Design Update, I noticed that many manufacturers of foil-faced bubble wrap were promoting their products for use under concrete slabs on grade. In this application, the shiny foil is clearly not facing an air space, so the exaggerated R-value claims made by bubble-wrap manufacturers were particularly outrageous. My article exposing the bubble-wrap scammers appeared in the September 2003 issue of EDU.
In that article, I reported that one manufacturer, WE International, made absurd claims about a thin (5/16-inch) product called Concrete Barrier rFoil. The manufacturer’s website boasted, “Concrete Barrier can serve three purposes underneath concrete: R-10 insulation, a vapor barrier and a radonColorless, odorless, short-lived radioactive gas that can seep into homes and result in lung cancer risk. Radon and its decay products emit cancer-causing alpha, beta, and gamma particles. barrier. … How does it compare to 2-inch foam board? It works just as well.”
Similarly, Insulation Solutions, the manufacturer of a 3/8-inch thick product called Insul-Tarp, claimed that the flexible tarp has an “R-value equivalent” rating of R-5 to R-10.
After these lies were publicized, three manufacturers wrote letters to EDU apologizing for the “oversights” and “typographical errors” that appeared on their websites.
Blurring the line between product R-values and assembly R-values
Many of the manufacturers and distributors that publish exaggerated R-values deliberately blur the bright legal line that separates product R-values from assembly R-values.
According to federal law, the R-value of an insulation product — for example, a piece of 1-inch thick polyisocyanurate — is the R-value of the insulation alone. That’s the R-value which insulation manufacturers are required to report on their packaging and in their advertising; the requirement is spelled out in the Federal R-Value Rule, a law that applies to manufacturers, retailers, and builders.
The R-value of a building assembly is something different. For example, if you build a wall with a layer of interior polyisocyanurate, followed by horizontal 1x4 strapping and drywall, the air space between the polyiso and the drywall has a measurable R-value. If you want to calculate the R-value of the entire wall assembly, you would need to calculate the R-value of the air space and add that R-value to the R-value of all the other layers. Once you’ve done that, you’ll know your wall assembly R-value.
Here’s the key point: polyiso manufacturers can’t claim the R-value of an air space in their labeling or advertising (unless the advertising makes a very clear distinction between the product R-value and the R-value of a hypothetical building assembly).
Product distributors are violating federal law
Fortunately, most (but not all) manufacturers of foil-faced bubble wrap have removed the blatant lies from their websites. Instead, manufacturers tempt the unwary with vague promises; for example, they claim that their bubble wrap “has a high R-value” or that it “resists the transfer of heat.”
The scoff-law websites with the greatest number of lies about foil-faced bubble wrap are those maintained by distributors — including a few large corporations like Home Depot, Ace Hardware, and Amazon — rather than those maintained by manufacturers.
For example, Amazon claims that a type of foil-faced bubble wrap product manufactured by EcoFoil (“HVAC Duct Wrap Insulation”) has an R-value of R-8. But a careful reading of the manufacturer’s technical data sheet and the referenced ICC-ES Evaluation Report reveals that the R-8 value claim is based on an assembly that includes the R-value of a 2-inch air space.
Similarly, Ace Hardware is advertising Reflectix, an R-1 foil-faced bubble wrap product, with a blurb that claims that the product has “R-values ranging from R-3.7 to R-21.”
That’s a little like Starbucks saying that a cup of coffee is a satisfying meal — as long as you remember to accompany the coffee with a 12-inch submarine sandwich (not included).
Yes, a few manufacturers are still lying
Although the major manufacturers of foil-faced bubble wrap have (almost) cleaned up their act, some still include exaggerations on their websites.
“Last September, the editors of Energy Design Update (EDU) questioned the astounding claims for R-value made by various manufacturers and distributors of foil-faced bubble pack insulation. Curiously, the November issue of EDU was full of qualifications from manufacturers, down-rating their R-value claims. To help resolve these competing claims, Canada Mortgage and Housing Corporation (CMHC) decided to fund a quick study on the actual installed performance of foil bubble pack and competing subslab insulations. ... The foil bubble pack tested was next to useless as subslab insulation.”
— Foil Bubble Pack: Subslab Insulation?
“The bubble-pack insulation had a low insulating value compared to the polyurethane panels and the XPSExtruded polystyrene. Highly insulating, water-resistant rigid foam insulation that is widely used above and below grade, such as on exterior walls and underneath concrete floor slabs. In North America, XPS is made with ozone-depleting HCFC-142b. XPS has higher density and R-value and lower vapor permeability than EPS rigid insulation. board. It’s cost benefit was the poorest of all insulating materials tested.”
— Canada Mortgage and Housing Corporation research report
“Manufacturers of reflective bubble pack insulations have claimed R-values for 5/16˝ thick duct wrap as high as 5.6. Independent testing of some manufacturers’ products has shown that the actual R-value is approximately 1.1 when the product is tested in accordance with ASTMAmerican Society for Testing and Materials. Not-for-profit international standards organization that provides a forum for the development and publication of voluntary technical standards for materials, products, systems, and services. Originally the American Society for Testing and Materials.
— NAIMA: Facts About the Performance of Reflective Bubble Pack Insulations in Duct System Applications
“We found no basis for the manufacturer’s claim of 77% reduction in heat loss due to Ultra CBF rFOIL in an under-slab application. This heat loss reduction significantly exceeds even that of 2-inch extruded polystyrene insulation installed under the full slab, while the insulating value of Ultra CBF rFOIL is much less.”
— Washington State University Extension Energy Program
One manufacturer that trumpets exaggerated R-values is EcoFoil (a.k.a. rFoil, a.k.a. Covertech Fabricating). The EcoFoil website describes the company’s duct wrap as an R-8 product, even though the R-8 claim is based on an assembly that includes an adjacent air space. The company also claims that “EcoFoil [foil-faced bubble wrap] under concrete insulation is superior to traditional, outdated forms of concrete floor insulation such as polystyrene or foam sheets.” This statement is false.
Elsewhere, EcoFoil claims that its 5/16-inch-thick bubble wrap product, which is called “Under Concrete Insulation,” has an R-value of R-3.8. It does not.
Another bad apple is Insulation4less, which retails a thin product called Prodex Total. On its website, the company states, “Prodex Total has a nominal thickness of 5 mm (13/64 inch) closed cell polyethylene foam covered on both sides with .0012 (00.03 mm) aluminum foil facing. ... R-value R-16 unaffected by humidity.”
Prodex may be unaffected by humidity — but it is seriously affected by gross exaggeration.
These are not examples of victimless crimes; there are victims. One victim is a blogger who reports using this sub-slab assembly: “In basement, install Insul-Tarp over crushed rock, single layer of wire mesh, and Wirsbro [hydronic] tubing, pour concrete (pump hose will go through stairwell hole).”
Unfortunately, Insul-Tarp has an R-value of R-2 or less. For years, however, the manufacturer of Insul-Tarp claimed that the product was rated at R-7 or more. The blogger who specified Insul-Tarp believed the false claims, which is why he wrote, “This is what the Insul-Tarp looks like. The exterior is some kind of tough fabric, then there are two layers of thin white foam, then a layer of bubble wrap. Hard to believe this can be equivalent of 2 inches of styrofoam.”
Indeed, it is hard to believe — so hard, in fact, that the Federal Trade Commission initiated court action that forced Meyer Enterprises, the manufacturer of Insul-Tarp, to stop making false claims. According to the FTC complaint, Meyer Enterprises “claimed Insul-Tarp’s R-value is 7.54, but in reality Insul-Tarp’s R-value could not be more than 2.”
Duct insulation scams
These days, most of the remaining confusion about foil-faced bubble wrap concerns duct insulation. As building codes ratchet up — many jurisdictions now require ducts to include R-8 insulation — manufacturers of bubble wrap have switched tactics. Instead of marketing their bubble wrap to concrete contractors, an increasing number of manufacturers are marketing bubble wrap to HVAC contractors as an easy-to-install duct insulation.
Online ads for “R-8 bubble wrap” lure unwary contractors into the marketers' net. Claims that bubble wrap can achieve R-4, R-6, or R-8 when used as duct insulation are based on a rarely attempted installation technique that requires contractors to install a series of spacers to maintain a consistent air space between the duct and the bubble wrap. This type of insulation is fussy and is unlikely to be durable. The manufacturers hardly care whether the assembly works, however, since they are basing their sales on obfuscations and contractors’ misunderstandings.
Few contractors bother to learn about the difference between product R-values and assembly R-values. A classic example of what’s going on at job sites around the country was described in a Q&A thread here at GBAGreenBuildingAdvisor.com: “Reflectix is still claiming R-4.2 for its bubble wrap, and my HVAC guy is hooked.”
The only remedy to these misunderstandings is the drumbeat of education. To stop these scams, energy experts need to educate building inspectors as well as contractors.
Martin Holladay’s previous blog: “When the Gas Pipeline Shuts Down.”
- Ace Hardware
- Image #8: Martin Holladay
Fri, 03/21/2014 - 06:47
Fri, 03/21/2014 - 07:09
Fri, 03/21/2014 - 08:42
Fri, 03/21/2014 - 08:57
Fri, 03/21/2014 - 09:03
Fri, 03/21/2014 - 09:33
Fri, 03/21/2014 - 10:49
Fri, 03/21/2014 - 10:52
Fri, 03/21/2014 - 10:52
Fri, 03/21/2014 - 11:11
Fri, 03/21/2014 - 12:21
Fri, 03/21/2014 - 13:22
Fri, 03/21/2014 - 13:26
Fri, 03/21/2014 - 16:18
Fri, 03/21/2014 - 17:10
Fri, 03/21/2014 - 17:22
Fri, 03/21/2014 - 19:21
Sat, 03/22/2014 - 07:55
Sat, 03/22/2014 - 11:21
Sat, 03/22/2014 - 20:40
Sun, 03/23/2014 - 13:31
Mon, 03/24/2014 - 06:03
Mon, 03/24/2014 - 11:20
Tue, 03/25/2014 - 18:53
Wed, 03/26/2014 - 04:50
Wed, 03/26/2014 - 17:37
Wed, 03/26/2014 - 17:42
Wed, 03/26/2014 - 17:59
Wed, 03/26/2014 - 18:33
Wed, 03/26/2014 - 18:36
Thu, 03/27/2014 - 11:01
Thu, 03/27/2014 - 11:09
Thu, 03/27/2014 - 11:31
Thu, 03/27/2014 - 11:34
Thu, 03/27/2014 - 11:54
Thu, 03/27/2014 - 13:24
Fri, 03/28/2014 - 22:27
Sat, 03/29/2014 - 05:24
Mon, 03/31/2014 - 08:46
Mon, 03/31/2014 - 09:09
Mon, 03/31/2014 - 09:37
Mon, 03/31/2014 - 09:43
Tue, 04/01/2014 - 14:03
Tue, 04/01/2014 - 14:21
Tue, 04/01/2014 - 15:08
Tue, 04/01/2014 - 16:13
Wed, 04/02/2014 - 11:46
Wed, 04/02/2014 - 11:59
Thu, 04/03/2014 - 09:38
Thu, 04/03/2014 - 11:49