Air leaks in houses are a big problem. Leaks make homes uncomfortable and expensive to heat and cool. They create condensing cold spots that attract mold and rot. They lead to frozen pipes and make homes less resilient during prolonged power outages.
Dealing with air leaks starts with locating them. There are many ways to find air leaks; the easiest and most common is to use a blower door. Blower-door tests used to be the exclusive domain of weatherization workers and building-science geeks, but that’s not the case anymore. Everyone involved in residential building needs to become more familiar with blower-door testing because universal testing for all new homes is coming.
Section N1102.4.1 of the 2012 International Residential Code (IRC) includes a requirement for blower-door testing with airtightness standards spelled out for the country’s various climate zones. New houses will need to meet or exceed these airtightness numbers to meet the current building code (see climate-zone map, below). It’s not clear who will do the testing, however. Some code-enforcement offices let contractors do their own blower-door tests. Others require third-party testing. It seems likely that some will have their inspectors do the testing.
How does a blower door work?
A blower door has a powerful variable-speed fan and a two-channel digital manometer, or air-pressure gauge. After being temporarily installed in an exterior door opening and turned on, it draws air from the house and blows it outside. The manometer measures both inside and outside air pressure.
For most of the tests, the idea is to register a 50-pascal (Pa) difference between the inside and outside air pressure using the blower door’s 3â„4-hp fan. The amount of air and fan power that it takes to register the 50-Pa difference corresponds to how tight or how leaky…