Is It OK to Close Air Conditioner Vents in Unused Rooms?
In most cases, the answer is no
Your air conditioner, heat pumpHeating and cooling system in which specialized refrigerant fluid in a sealed system is alternately evaporated and condensed, changing its state from liquid to vapor by altering its pressure; this phase change allows heat to be transferred into or out of the house. See air-source heat pump and ground-source heat pump., or furnace probably uses a lot of energy. Heating and cooling makes up about half of the total energy use in a typical house. For air conditioners and heat pumps using electricity generated in fossil-fuel fired power plants, the amount you use at home may be only a third of the total. A question I get asked frequently is whether or not it's OK to close vents in unused rooms to save money. The answer may surprise you.
The photo on the right shows a typical supply vent for an ducted HVAC(Heating, ventilation, and air conditioning). Collectively, the mechanical systems that heat, ventilate, and cool a building. system (air conditioner, heat pump, or furnace). On the return side, you'll typically see plain grilles, but on the supply side, where the conditioned air gets blown back into the house, most HVAC contractors install registers like the one above. It has a lever of some sort that allows you to adjust the louvers behind the grille.
You'd think that since it's adjustable, it must be OK to open or close it to suit your needs, right?
The blower and the blown
The blower in your HVAC system is the heart of the air distribution. It pulls air from the house through the return ducts and then pushes it back into the house through the supply ducts. In high-efficiency systems, the blower is powered by an electronically commutated motor (ECM), which can adjust its speed to varying conditions. The majority of blowers, however, are of the permanent split capacitor (PSC) type, which is not a variable-speed motor.
In either case, the system is designed for the blower to push against some maximum pressure difference. That number is typically 0.5 inches of water column (iwc). If the filter gets too dirty or the supply ducts are too restrictive, the blower pushes against a higher pressure.
In the case of the ECM, a high pressure will cause the motor will ramp up in an attempt to maintain proper air flow. An ECM is much more efficient than a PSC motor under ideal conditions, but as it ramps up to work against higher pressure, you lose that efficiency. You still get the air flow (maybe), but it costs you more.
The PSC motor, on the other hand, will keep spinning but at lower speeds as the pressure goes up. Thus, higher pressure means less air flow, and, as we’ll see below, low air flow can cause some serious problems.
The important thing to remember here is that no matter which type of blower motor your HVAC system has, it's not a good thing when it has to push against a higher pressure.
Closed registers increase pressure
In a well-designed system, the blower moves the air against a pressure that's no greater than the maximum specified by the manufacturer (typically 0.5 iwc). The ideal system also has low duct leakage.
The typical system, however, is far from ideal. Although most systems are rated for 0.5 iwc, the National Comfort Institute, which has measured static pressure and air flow in a lot of systems, finds the typical system to be pushing against a static pressure of about 0.8 iwc. Now we're ready to address the question of closing registers.
When you start closing registers in unused rooms, you make the duct system more restrictive. The pressure increases, and that means an ECM blower will ramp up to keep air flow up, whereas a PSC blower will move less air. Most homes don't have sealed ducts either, so the higher pressure in the duct system will mean more duct leakage, as shown in Image #3 below.
The more registers you close, the higher the pressure in the duct system goes. The ECM blower will use more and more energy as you do so. The PSC blower will move less conditioned air. In both cases, the duct leakage will increase further.
What about heat?
In addition to moving air, your air conditioner, heat pump, or furnace is also cooling or heating that air that flows through the system. The air passes over a coil or heat exchangerDevice that transfers heat from one material or medium to another. An air-to-air heat exchanger, or heat-recovery ventilator, transfers heat from one airstream to another. A copper-pipe heat exchanger in a solar water-heater tank transfers heat from the heat-transfer fluid circulating through a solar collector to the potable water in the storage tank. and either gives up heat or picks up heat.
In a fixed-capacity system — and most are — the amount of heat the coil or heat exchanger is capable of absorbing or giving up is fixed. When the air flow goes down, less heat exchange happens with the air. As a result, the temperature of the coil or heat exchanger changes.
If air flow is low, it'll dump less heat into the coil in summer, and the coil will get colder. If there's water vapor in the air, the condensation on the coil may start freezing. You might even end up with a block of ice, as shown in the photo below. And ice on the coil is really bad for air flow.
It's also bad for the compressor, as not all of the refrigerant evaporates and liquid refrigerant makes its way back to the compressor. If you want to have to buy a new compressor, this is a good way to do it.
The same thing happens if you have low air flow over a heat pump coil in winter. You could get a really hot coil, high refrigerant pressure, and a blown compressor or refrigerant leaks.
Similarly, low air flow in a furnace can get the heat exchanger hot enough to cause cracks. Those cracks, then, allow exhaust gases to mix with your conditioned air. When that happens, your duct system can become a poison distribution system as it could be sending carbon monoxide into your home.
Nine unintended consequences of closing registers
Let me now summarize the problems I've described above that can result from closing registers in your home. The first thing that happens is the air pressure in the duct system increases, which may give rise to these negative consequences:
- Increased duct leakage
- Lower air flow (with PSC blowers)
- Increased energy use (with ECM blowers)
- Comfort problems because of low air flow
- Frozen air conditioner coil
- Dead compressor
- Cracked heat exchanger, with the potential for getting carbon monoxide in your home
- Increased infiltration/exfiltration due to unbalanced leakage , as I described last week
- Condensation and mold growth in winter due to lower surface temperatures in rooms with closed registers.
You're not guaranteed to get all the problems that apply to your system, but why take the chance?
A Kickstarter project to avoid
I recently wrote about all the IT folks who are trying to follow in Nest's footsteps and profit from the home energy-efficiency movement. I used the Aros smart window air conditioner as the example of companies that think you can solve problems just by creating a product with a smartphone app.
Well, meet a more malignant idea: the E-vent. (You can find it easily enough by searching on the term "Kickstarter E-Vent.") It's just a Kickstarter project right now, and maybe it won't get funded. If it does get funded, however, it will be subject to all the problems I described above. It doesn't matter whether you close the registers by getting up on a ladder in your home or from the beach in Cozumel. It's still a bad idea.
The E-Vent page on Kickstarter says that the device will monitor the air temperature and open registers if the temperature gets too cold (while air conditioning) or too hot (while heating). Of course, that’s not going to work unless they monitor the temperature right at the coil or heat exchanger. And that still probably wouldn’t work, because there’s a wide range of acceptable temperatures for different systems.
This is an HVAC product developed by people who don't know some very important principles of heating and air conditioning. Let's hope they don't kill anyone.
The only way that closing registers could work
The fundamental problem here is that closing supply registers in your HVAC system changes what comes out in particular locations. It doesn't change what the blower is trying to do. Nor does it change the amount of heat that the air conditioner, heat pump, or furnace is trying to move or produce.
Yes, your system may be fine if you close a register or two in your home, but the results will depend on how restrictive and leaky your duct system is. If it’s a typical duct system with 60% higher static pressure than the maximum specified, closing even one register could send the system over the edge. If it’s a well designed system with low static pressure and sealed ducts, you shouldn’t have a problem — as long as you don’t try to close too many registers.
The only way that something like this could work is if closing a register signaled the blower to move less air and the air conditioner, heat pump, or furnace to move or produce less heat. (Properly designed zoned duct systems do this by using variable speed ECM blowers with multi-stage systems.) Otherwise you're subject to those nine unintended consequences, one of them potentially deadly.
Allison Bailes of Decatur, Georgia, is a speaker, writer, energy consultant, RESNET-certified trainer, and the author of the Energy Vanguard Blog. Check out his in-depth course, Mastering Building Science at Heatspring Learning Institute, and follow him on Twitter at @EnergyVanguard.
Thanks to Curt Kinder, David Butler, John Semmelhack, Eric Sandeen, and Dale Sherman for suggestions that made this article better and more complete.
- Energy Vanguard
- HVAC Hacks and Other Screwups
- Circle Design Technology
Wed, 07/30/2014 - 09:47
Wed, 07/30/2014 - 10:54
Wed, 07/30/2014 - 11:10
Wed, 07/30/2014 - 14:29
Wed, 07/30/2014 - 14:51
Wed, 07/30/2014 - 16:27
Wed, 07/30/2014 - 16:31
Wed, 07/30/2014 - 16:44
Wed, 07/30/2014 - 16:46
Thu, 07/31/2014 - 14:59
Sun, 08/03/2014 - 10:39
Mon, 08/04/2014 - 17:08
Mon, 08/04/2014 - 22:54
Wed, 08/06/2014 - 11:23
Fri, 08/08/2014 - 11:57